Application and Dosage
One 1 pint bottle of Cleaner F3 is sufficient to clean a typical domestic central heating system (average 3 to 4 bedroom house or 100 litres). Additional/repeat applications of Cleaner F3 may be necessary for larger systems, or if systems are heavily sludged. First drain and refill the entire system with plain water. For optimum results the entire system, including drop feed radiators where fitted, should be completely drainable. Preferably, full bore gate valves with hose connectors should be provided temporarily for this purpose. Motorised and thermostatically controlled valves must be set so that no part of the system is closed off during cleansing or rinsing. Discharges must be made to the foul drain and not the surface water drain.
Colour: Dark amber
pH (conc): 7.0 – 7.5
pH (0.5% soln) 7.5 – 7.8
SG: 1.20 @ 68°F
Packaging, Handling and Storage
Fernox Cleaner F3 is supplied in 1 pint containers. Fernox Cleaner F3 is not classified as hazardous but, as with all chemicals, care should be taken. Do not mix with any other chemicals other than Fernox products stated. Keep out of the reach of children.